Inline Dimmable Responder that adds INSTEON control to overhead lights. Requires installation by a qualified electrical contractor.
View the Insteon DIN-Rail Dimmer on the Insteon integration diagram
- DIN-rail mounted for ordered, easy to access installation
- Input terminals for optional manual switch control
- Compatible with latching and single/dual momentary switches
32 Dimming Steps
Easy DIN rail installation
When planning the electrical wiring for your home or business, avoid adding too many wall switches in a single location. Wall switches ganged together cause homeowner confusion and can quickly ruin the aesthetic of a room. Instead consider adding a single INSTEON controller to control all the lighting. It's easy when combined with INSTEON DIN Rail products.
The DIN Rail Dimmer module clips directly onto a 35mm DIN rail and wires to load, power and neutral. Link it to an INSTEON keypad or any other INSTEON device for full remote control over the module and it's connected load. Specifically, DIN Rail On/Off is compatible with the "Top hat rail EN50022" (sometimes referred to as a Type O or Type Ω) The DIN Rail On/Off will fit either variation of this style DIN rail (either 15 or 7.5 mm "high" off the mounting surface).
What is a DIN rail?
A DIN rail is is simply a metal rail on which compatible products (circuit breakers, switches, etc.) can be snapped on to. Common electrical switch-boards and enclosures have a DIN rail behind the devices. The DIN rail can simply be mounted to any flat surface (or even across studs).
This product must be installed by a licensed electrical contractor.
|Product Name:||INSTEON DIN-Rail Dimmer|
|Regions:||Australia and New Zealand|
|In the box:||INSTEON Inline Dimmer - DIN|
|INSTEON:||Controller and responder|
|Load brightness levels:||32 locally (256 with software)|
|Status LED:||Green when load is on, red when load is off, Blinks green or red during setup, Blinks red once when responder does not acknowledge/blinks green once if all responders acknowledge (can be disabled via software)|
|LED brightness:||Adjustable from off to 100% bright|
|Local ramp rate:||Adjustable from 0.1 second to 5 seconds locally (0.1 seconds to 8 minutes with software)|
|Commands supported as controller:||On / Off, Fast on / Fast off, Begin brighten / End brighten, Begin dim / End dim|
|Commands supported as responder:||On / Off, Fast on / Fast off, Begin brighten / End brighten, Begin dim / End dim, Incremental brighten / Incremental dim, Beep|
|RF range:||45m +|
|Phase detect beacon:||Yes|
|X10 addresses:||Any 1 of 256 (unassigned by default)|
|INSTEON device category:||0x01 dimmable lighting control|
|INSTEON device subcategory:||2453-222 (921MHz), 0x34|
|Status LED:||Green. Blinks on activation|
|Sense Modes:||Jumper Installed: Open = Group 1 On, Closed = Group 1 Off; Jumper Uninstalled: Open = Group 1 On (or off), Closed = Group 2 On (or Off)|
|Aux. Sensor Input:||Senses contact closure|
|Aux. Sensor Input Wire:||>= 20 gauge wire|
|Setup Memory:||Non-volatile EEPROM|
|Mounting:||35mm (top hat) DIN rail||Max. cable size:||4mm˛, 12 AWG (2.72mm diameter)|
|Min. cable size:||1.5mm˛, 15 AWG|
|Screw DIN rail connections:||Line, Neutral, Load, Sense 1, Sense 2||Casing:||UV stabalized plastic (INSTEON White)||Set button:||Yes||Beeper:||Yes||Beep on button press:||Optional (off by default)||LED:||1 RGB|
|Dimensions:||80mm W x 53mm H x 63mm D|
|Operating Conditions:||Indoors, 0° C to 40° F, up to 85% relative humidity|
|Voltage:||100VAC to 240VAC|
|Frequency:||50/60Hz auto-detected at power-up|
|Max. load:||300W at 100-240VAC|
|User replaceable fuse:||Yes (16 A (T)) 5x20mm fuse|
|Retain all settings without power:||Yes, saved in non-volatile EEPROM|
|Standby power consumption:||<1W|
|Certification:||Approved for use in Australia and New Zealand|
Products similar to the Insteon DIN-Rail Dimmer:
Dimmable Micro-Module Responder that adds INSTEON control to overhead lights. Installs behind a light switch.
Inline On/Off Responder that adds INSTEON control to a fixed on/off appliance or non-dimmable lighting zone. Requires installation by a qualified electrical contractor.